Share this story:
View & download the full report at www.TexASCE.org/beyond-storms.
In the early morning hours of February 15, 2021, most Texans were sleeping soundly, resigned to the reality of the extreme winter weather from Winter Storms Uri and Viola were battering every corner of Texas, but comforted in the belief that the electric system was reliable with service available at the flick of a switch. In reality, reliability and resilience were not in balance, it was teetering on the edge. A series of problems overwhelmed the fragile balance and turmoil cascaded through every sector of the essential infrastructure serving Texas.
The scale of the tragedy that emerged in the storms’ aftermath included more than 200 Texans who lost their lives and substantial and lingering economic impact to the entire region that has been estimated to exceed $200 – $300 billion[i] in addition to disputes and securitizations. The economic impact of Uri and Viola was greater than the impact from either of the two most costly hurricanes[ii] in US history, Harvey ($145B) or Katrina ($161B). In comparison, in 2019 Texans spent around $37 billion on retail power during the entire year[iii]. Regardless of the metric, from public safety to economic impact, Uri and Viola deserve a comprehensive response to prevent recurrence. Starting during the peak of the storms, the members of the Texas Section of ASCE volunteered to begin work to unravel what happened and develop such a response—the ASCE Texas Beyond Storms Infrastructure Network Resilience Task Committee.
There is no effective tool to allocate specific responsibility of what impacts were directly from the weather itself, what was directly impacted by the failure of the electric system, and what were indirect impacts. However, ASCE believes that the failure of the electricity grid was directly and indirectly a material contributor to the economic harm and human tragedy experienced from the Winter Storms. This Committee also determined that the problems uncovered by the severe storm extend well beyond storm related issues. Texas has a substantial and growing electric system reliability and resilience problem.
A reliable and resilient electric system in an increasingly electrified economy is critical to the safety and economic health of all Texans. There is a view that reliability deterioration is an inevitable part of the “cost of transition” underway in the energy sector. Due to the extreme costs of reliability failure, it is reckless to believe that the energy market transition should somehow be used as justification for reliability declines and extended load shedding events. For energy transition to work effectively and be accepted, it must occur without any sacrifice to reliability and resilience. ASCE Texas Section’s urgency is driven by the conclusion that the failures that caused overwhelming human and economic suffering felt last February will increase in frequency and duration due to legacy market design shortcomings, growing infrastructure interdependence, and economic and population growth drivers, even if the frequency and severity of weather events remains unchanged.
Critical infrastructure requires large, routine capital expenditures to support expansion, maintenance, and operations to meet demand, also known as Revenue Sufficiency. Policies, regulations, and market actions that distort, constrain, or negatively impact the flow of capital to needed investment starves reliability through deferred expansions, delayed maintenance, and reduced reliability investment. This pattern of deferral and avoidance, results in a costly “run to failure” outcome followed by surprise that reliability and resilience was somehow compromised. It also answers some of the most troubling questions identified during the analysis:
- Why did the critical fail-safe fail to perform when needed?
- Why did most natural gas fueled electric generators rely upon some combination of interruptible gas supply and/or transportation to serve winter peak demand?
- Why did the gas industry experience wide-spread production declines?
To understand the root cause of the Winter Storm Uri and Viola and Viola problems, it was necessary to look beyond (1) the physical infrastructure and include (2) the impact of regulations that apply to the use of the infrastructure, and (3) the markets themselves. The energy infrastructure system works or fails by how well these three legs of the energy market work together. In analyzing this “Energy Market Stool,” ASCE identified two related problems: 1) a failure to support reliable dispatchable power generation and 2) the negative impact from sources of intermittent subsidized electric power generation. This assessment concludes that:
- revenue insufficiency from ERCOT’s energy-only market model, influenced by federal and state subsidization of intermittent resources, fails to adequately pay for reliable dispatchable generation, and
- these market model deficiencies are the leading contributor to making the ERCOT system less reliable.
The next most consequential contributor to reliability degradation is the relentless creep of interdependence between infrastructure sectors, which contributes to increasing the fragility of each system(s) and sets the stage for cascading failures across sectors. Interdependence occurs when the reliability of one sector is mutually dependent on the reliable performance of another sector. The impacts of interdependence will continue to deteriorate reliability without action – but proactive steps can be taken. It can be mitigated, fragility improved, and reliability enhanced by implementing a series of actions that are:
- relatively modest in scale,
- focus on enhancing reliability of ERCOT, and
- mitigate the interdependence risk between infrastructure sectors.
The two remaining key contributors to reliability degradation work in more subtle ways. These two contributors include rules, policies, and regulations that create negative impacts to reliability instead of enhancing them, resulting in a legacy ERCOT philosophy and culture that has prioritized low cost to the detriment of reliability.
Determining the costs to rectify these problems is a very complex issue. However, a simplified, approach[iv] considered an existing capacity-based power market structure that explicitly pays for reliability for an indicative answer, expects < 5% increase to prices in ERCOT. This relatively modest level of notional investment for the benefits of improved reliability and resilience compared to the recent cost of failing to prioritize reliability is overwhelming.
There are five (5) Network Recommendations for focused improvements:
- Invest in black start generation to ensure reliable and fail-safe dispatchable back-up power.
- Restructure regulatory flaws negatively impacting dispatchable generation reliability.
- Mitigate growing interdependency between infrastructure sectors.
- Prioritize reliability focused regulations and incentives and eliminate regulations that include the unintended consequences of creating negative impacts to reliability.
- Replace process and model bias and failures and the narrow pursuit of short-term price reductions with a reliability and resilience driven culture and prioritization at ERCOT.
These 5 recommendations along with a summary of recommendations for the water and wastewater, telecommunications, transportation, electricity, and energy sectors are included in the Executive Summary and a full report now available for download on at www.TexASCE.org/beyond-storms.
[i] The Perryman Group (2021), Preliminary Estimate of Economic Costs of the February 2021 Texas Winter Storm, February 2021. (low case = $197.2B, High case= $295.8B)
[ii] The Perryman Group (2017), Preliminary Estimate of Economic Costs of Hurricane Harvey, August 31, 2017 ($145B). and NOAA.gov Office of Coastal Management, Fast Facts – Hurricane Costs
[iv] T Popik and R Humphrys (2021). The 2021 Texas Blackouts: Causes, Consequences, and Cures. Paper and presentation The Journal of Critical Infrastructure Policy, spring/summer 2021
Share this story: